The TE-8 expanded metal system combines the high-quality appearance of a suspension cassette with a low-cost substructure and fast installation.
Expanded metal ceiling TE-8
elo. verz. steel
Fire protection class:
A2-s1, d0, DIN EN 13501-1,
with bonded fleece: A2-s2, d0, DIN EN 13501-1
The TE-8 expanded metal system uses a T24 rail construction common to drywall but concealed, making both the substructure itself and the installation of the overall ceiling particularly economical and efficient – but all with the appearance of a drop-in cassette.
T24 support rails with quick-action tensioning hangers must be suspended plumb and flush from the bare ceiling at a center distance of 1200/1250 mm by means of approved dowels, screws, etc. The distance between centers must not exceed 1200/1250 mm. The suspension distance must not exceed 1200/1250 mm in the axial direction. Between the main rails, the cross rails 1200/1250 mm long are clipped in at an angle of 90° at a center distance of 600/625 mm. The TE-8 cassettes must then be hooked into the substructure in such a way that they can be removed at any time.
The laying mark must always be in the same direction. A checkerboard pattern on the ceiling caused by twisted panels must be avoided and will not be accepted.
The expanded metal cassettes are usually cut to size on site. The edge connection is made using a system-compliant stepped wall angle.
We will be happy to advise you individually based on your object.
Care and cleaning instructions:
Pagolux®-Streckmetalldecken sind wie folgt zu reinigen:
Clean surfaces with slightly damp cloth and then dry with soft cloth.
- Use only pure water, if necessary with small additions of neutral or weakly alkaline detergents.
- Use only soft, non-abrasive cloths.
- Do not use steam jets or high-pressure cleaners.
- Do not use scratching, abrasive agents.
- Avoid vigorous rubbing.
- Always carry out preliminary tests on non-visible surfaces before cleaning.